Boiler water chemistry - Properties of feed water explored - Bright H
Feb 01, 2016 · Boiler water with a pH of 10.5 contributes 12.6mg/l towards the boiler TDS, whilst at a pH of 12.0 it increases to 400mg/l and at 12.5pH the value is 1264.9 mg/l, a whopping 100 fold increase.
Jun 24, 2014 · If the pH is lower than that, the water will start eating the pipes. If it's higher than that, the water won't corrode metal, but it may begin to foam, and that's not good. Hold that thought for a moment. You're on a job and you have a steam boiler that's taking on a lot of feed water …
Common Chemicals Used in Boiler Water Treatment
Nov 07, 2016 · Keep the corrosion to a minimum in your steam boiler? Keep the pH between 8.5 and 9.5Here is how you check the pH of your boiler water.Easily done. No proble
Controlling pH. pH is controlled by either removing water impurities or adding other chemicals to neutralize the condition. For example, Caustic Soda, an alkaline, is added to neutralize CO3, carbonic acid. pH Related Corrosion. Acid Attack. When the boiler water pH drops below about 8.5, a corrosion called acid attack can occur.
Below a pH of 5.0 the water is acidic enough to dissolve the steel boiler plates. Under these conditions the steel gradually becomes thinner and thinner until its destruction. At a pH between 5 and 9.4 pitting of shell plates will occur at a rate depending on the amount of dissolved oxygen in the boiler.
Common Chemicals Used in Boiler Water Treatment - Sensorex